coils still icing-up and won't cool. cleaned coils and new filterstill no cool and ices up.
Type of HVAC: Thermostat Control
cleaned coils, changed to new filter.
Hello and welcome to Just Answer. I am servtech50 and will assist you today.
Does your system ice up from outside in? or just the coil begins to ice up?
If the frost/freezing starts outside the evap coil usually means a dirty filter or blower not up to speed. I do see you replaced the filter. if only coil freezes up then either you are low on refrigerant.......or the metering device is not feeding correctly........or the metering device is partially plugged, like with some solider that broke lose.
over 20 yrs. experience
What Happens Now?Your chat has ended, but you can still work with your Expert to get an answer to your question if you have not yet received one.Come back to this page at any time to see additional information from your Expert. You will also receive an email when your question is updated. If you want to send a message to your Expert, use the box below.If you have already received a satisfactory answer to your question, click the Accept button above. Experts are credited for each accepted answer they provide.
Sorry droid feezing up, just want confirmation, inside coils freezing up so either low refrigerantor some blockage at metering device or coolantlines..?
yes you are correct. It will be on or the other.