HVAC Questions? Ask an HVAC Expert for Answers ASAP
Hello I'm Norman & thanks for using JustAnswer. Please do not press accept or leave feedback until you feel we have reached a resolution. Watch the back of the actuator where the spindle/shaft goes, if it moves the valve is bad again. If it doesn't move the actuator is bad.
Hello Norman, thanks for your reply to my motorised vave problem. after removing the actuator from the vave and switching the timer i noticed that the actuator is turning but then starts clicking as if it wants to turn further also i am able to turn the spindle on the two port valve with my fingers it dose not seem to be stiff or seized.
Yes it sounds like your actuator needs to be replaced. The sound your hearing is a stripped gear.
Hi Norman,Thanks for your advice. i will replace the actuator.Thanks, Dave.
No problem Mr. Howard. Please feel free to message me again if you should have any further questions.