Turn power off to furnace and wait 30 seconds and turn back on retry furnace. let me know if it goes thru sequence of operation. Small fan start for 15 to 20 seconds ,igniter glows for 10 seconds and burner lites. Russ
ok. trying now
7 flashes is the flanes was not senses. Will try to relite and go inot one hour lockout. Russ
Sorry flame not sensed. Russ
what does that mean exactly?
still blinking 7 times. does that mean I need a new element
or is my furnace completely shot
The furnaces tries to lite and the flame sensor does not sense a flame. If you look at burners you will see a small sensor inserted into burner. It is a very thick wire and has one lead attached. This is sensor. Remove sensor clean with sand paper and reinstall. Retry furnace. This is a common problem. The sensor gets corroded and will not sense flame. Russ
No try to clean sensor first. Russ
I dont know where to look for the sensor7
If you look at burners it will be on left side. You will see one wire attached to spade terminal.
nothing on the left. on the right there are 2 wires, 1 on top, 1 on bottom
now light is blinking 5 times
Give me a moment to check code.
That is rollout switch open .. Look on top of burner for a small disk about size of quarter. It will have reset this button. Reset and retry furnace.
I have to leave so I will opt out for another expert. He will need model number of furnace. Russ
ok. there is no small disk. model number:G9T06010UPB13C
I dont know anything about furnaces
would i see flame where the little window is in the burner unit?