Hello my name is XXXXX XXXXX will be my pleasure to assist you. First thing to do is go to the furnace take off the lower blower door and locate the circuit board turn the power off to the furnace. In the circuit board there should ba a small car like fuse usually 3 or 5 amps check the fuse it is probably blown replace the fuse with the same amperage fuse and then turn the power back on on the furnace and check the operation of the furnace.
I understand what you are saying. I have turned off the power and located the circuit board, but I don't see the fuse. Would it be enclosed in in something? I don't see it on the diagram either.
No it shouold be right in the circuit board pushed into it.
There should be a fuse somewhere that protects the low voltage side of the transformer. That sounds like what is blown that is why the blower won't come on when you put the thermostat fan switch in the on position.
Could be can you take a picture and post it so I can get a better look at it.
Here is a pic of the control panel and the fuse links
The things you are calling a fuse links are actually flame rollout switches. Most times these have a red reset button on the back between the wires if pressed in it resets the switch. I didn't see the reset in the pictures. If you have access to an electric meter with the power off set the meter to ohms and check to see if the switches are open. or you can us an unbent paper clip and take the wires off the switches and us the paperclip to jump the two wires together. If the furnace fires with the blower dooron and the switches jumped then the switch is bad and will need to be replaced.
Trying using the paper clip at the circuit board to jump the red or R terminal to the W terminal and then press the door switch in and see if the furnace fires.
it has to be the circuit board then Is there an inducer motor near where the chimmney attaches to the furnace?\
Is there a way you can try and turn it to see if it spins freely?