HVAC Questions? Ask an HVAC Expert for Answers ASAP
does the burner ever actually fire when this code appears?
So we dont have all the time: exhaust starts, flame lights, flame goes out.
And we also dont have exhaust starts, flame never lights all the time?
We a combination of lighting and not lighting all with the slow altrenating flash?
It starts, runs for a little bit, then goes out.
Yes, combination of lighting and lighting.
First check all the ground wires. Furnace to board and furnace to incoming ground.
If the ground wires are all tight and intact, then it would point to poor ignition circuitry in the board.
I have checked ground circuits. How do I check circuitry in the board?
The field testing is somewhat limited as circuit boards are not field repairable.
however here is a service manual to assist you in troubleshooting.
I believe you will find itto be circuit board if indeed the code is always the same...unit lights and does not light, and grounds and sensor check ok.
Link - http://www.cozyparts.com/Lennox-Parts/forum/Lennox_service_manual/Furnaces/G32V_02-01-2004.pdf