I just verified the control. The light is on constant when powered. The following is the fault code arrangement.
SYSTEM LOCKOUT FEATURES
When system lockout occurs, the gas valve is de-energized, the
circulator blower is energized at heat speed, and, if flame is
sensed, the inducer blower is energized. The diagnostic indicator
light will flash or glow continuously to indicate system status.
(System lockout will never override the precautionary features.)
If the sensed failure is in the system (external to the control), the
LED will flash in the following flash-pause sequences to indicate
failure status (each flash will last approximately 0.25 seconds,
and each pause will last approximately 2 seconds).
1 flash, then pause System lockout
2 flashes, then pause Pressure switch stuck closed
3 flashes, then pause Pressure switch stuck open
4 flashes, then pause Open limit switch
5 flashes, then pause Open rollout switch
6 flashes, then pause 115 Volt AC power reversed/Improper
7 flashes, then pause Low flame sense signal
Continuous flashing Flame has been sensed when
(no pause) no flame should be present (no
call for heat)
The LED will also flash once at power-up.