The wait is 5 minute time delay. Give it few minutes and get back to me if it is not working. Need model number of thermostat. Russ
yes but I also noticed last night that it would come on and off (the cooling unit) while the heat pump was still running outside seemed like it was cutting off. It is a Honeywell Touchscreen Thermostat there is not model number on it will look behind faceplate too see.
There is a bar code behind the faceplate but nowhere is there a model name or number barcode number is XXXXX
could the thermostat just be defective?
still only activating heat pump.
What is make and model number inside equipment. May be a fan board problem. Russ
7-Day Programmable Thermostat - RTH7600D
I sorry I mean the air handler. Russ
The air handler is the internal unit right not the Trane on the exterior of the house?
Yes air handler is on inside, Russ
air handling unit model#TWE060P13FBO Air handling unit serial # XXXXX
I have a 10 year warranty on compressor as all was installed in 2003
Turn fan to on position and see if it runs. Russ
it does not
no go in on position
I am a Trane Service Manager. We will one step at a time. Open blower door and feel motor to see if it is hot. Also inspect the capacitor(small silver cannister on the blower housing. Russ
this is the exterior trane unit or the interior air handler
Interior unit top panel. Russ
Russ, it sounds like I need a service call wouldn't you say. I am in Florida and my air handler is in the attic. Went up there yesterday and it was hotter than hell gotta bring in a ladder etc...old house. Even if I go up there we are just going to determine that it probably needs service right? If you agree I will accept your advice and call in for service.
To darn hot to get up there. The older I get the hotter the attics get. Better to call a service tech. But sounds like on of three things ,fan relay,capacitor or motor. Russ
thank you for determining it is not the thermostat