HVAC Questions? Ask an HVAC Expert for Answers ASAP
Hello my name is Heath it will be my pleasure to assist you. You will have to hold the button down on the burner for thirty to sixty seconds then the burner will start but you will have to bleed the air from the small 3/8 nippl on the left side of the pump toward the bottom. Open the port and have a container to catch the oil because once its open oil will come from the port as well as air. If the pupmp shuts down be sure and close the port so no air gets back in. You may have to bleed the air a couple times by holding the reset button down for thirty to sixty seconds again to get the burner to start.
When I open the nipple, no oil comes out. I had it refilled today.
Also, I held the button down for 30-60 seconds and no go...
The only light on is one solid red light.
Yes you will have to hold the button down longer and then when the motor starts open the nipple and fuel and air will come out once the motor starts. You are pressing the red button just above the red light right?
I am pressing the only button I see there, just above the red light. I held that button down for 2 minutes with no response. I am perplexed.
Try resetting the power first then hold the button down after the power has been reset.
I tried that...
What type of burner is it Example: beckett, reillo, miller
Mclain Gold Oil Boiler
Thats the name of the boiler the burner is made by someone else there should be a name on it.
Marathan Electric from Wisconsin
Does the reset box have terminals T and T?
Are they combined together with a jumper?