Wiring schematic for a Honeywell Protectorelay oil burner control to connect cad cell and burner 25 year old no model number
Make : Honeywell
can't wire without some help 3 wires orange black white?
Welcome to Just Answer, I will do my best to help you solve your problem
Do you want to know how to wire it or do you want the internal schematic?
Just the schematic will do thank you
I don't have an internal schematic for a 25 year old ignition control, I can tell you how to wire it
Tie the whites together, black to the hot side of the incoming power feed, orange to the burner motor and transformer
Thanks that will work I'm sure. Phil
40+ years experience licensed oil & gas tech