HVAC Questions? Ask an HVAC Expert for Answers ASAP
It may have J wire running thru heat relayl Ther should be switch on thermostat that saysa el/gas. Flip to ele. Russ
no such switch on the stat.
left side has: auto/on for fan
right side has:off/cool/auto/heat/emer
BTW this unit has been installed and running for 5yrs and I've just realized that the strips are not coming on. I am really trying to determine if the stat is bad-or wired wrong. I'm satisfied that the strips are working when powered up.
We just had the coldest weather since installation, so it may have been wrong all along.
NOTE it is listed in original question. Here it is again.
HONEYWELL Y594G1252 - ATTACHED TO:
Note also that I powered up the strips manually by applying 24v to the contactor coil brown wire. he contactor pulled in, the fan came on, and immediately every smoke detector in the entire house began to go off- as lint was being burned from the strips.
Just need to wiring diagram for furnace. Can I have model number of air handler. Also try fan to on position and turn up heat to see if it works. Russ
Nordyne split system heat pump.
Fan in on position and turning up heat does not make strips come in.
this is the print for the heat coils
@ work still looking for the handler model #
24v not present across the limit.