HVAC Questions? Ask an HVAC Expert for Answers ASAP
Sorry for delay...very busy last couple days. Do you still need assistance?
Ok...code 34..flame fault.
Exhaust motor starts....then what? Does ignitor glow?....any flames...?
Thank you.....does the gas valve click?....does it sound like gas enters the burner?
can't say that i hear a click what should i look/listen for exactly
Here is what should be...
exhaust fan starts
30 seconds later gas valve clicks and gas enteres burner
If no flame in 3 seconds then code 34 appears
since you have glow the options are as follows..
you have gas entering burner but ignitor is not hot enough
you do not have gas
you have bad gas valve
you frozen gas meter or regulator
You can undo a pipe by furnace to see if gas is available.