Hello my name is XXXXX XXXXX will be my pleasure to assist you. The blower motor will need to be changed as the fan speed that is on the heat is burned out The one for the on position a different speed you could look in the furnace and locate the blower wire that is on the heat terminal of the board and then find one that is on park and switch the two and see if the blower runs if it does then the motor is bad if not then the board is bad not getting power to the heat winding of the blower.
The wires from the blower go to the circuit board in the furnace. Turn off the power before you switch the wires. There is one indoor blower that is what I am talking about and it is a 3 or 4 speed motor if the speed that is on heat is burned out and the other speeds are okay you may be able to use another speed. That is what I am trying to get you to switch the wires for.
ok Heath. I'll try what you are suggesting.I'll let you know. Also, is it a big deal to change the motor if needed? I'll let you know in the A M .
No its not that big a deal to change the motr the worst part is getting the squirrel cage off the motor shaft. But I can get you through it.
Hi Heath: I found the red wire under a angle flange protector and switched with both the brown and yellow unused wires. Neither one would work,so I'm assuming the blower motor is shot. Altho I think I can r/r the blower motor, I think I'll have a proffessional take care of that. Tell me what you think.
Yes the blower motor is shot you will need to replace it. Its really not that hard to change the worst part is getting the squirrel cge off the shaft of the motor.