Have HVAC Questions? Ask an HVAC Expert for Answers
What is model number of inside unit. Russ
it is not an inside unit, its central air..and it was working fine, it still is cooling just not removing the humididty
amana 1 ton vccc204c2c
You may have to lower fan speed. That will remove more moisture. It will cause the coil to be colder and more water will condense. Russ
where do i find the fan speed control
That model number does not come up. Do you have remote for this unit. Russ
sorry Russ there wasnt a 0 in there..its vcc24c2c
and no there is no remote unit...I just have a sm ranch home..and my central air is 6 yrs old...
You will have to go into inside unit and change fan speed. You w ill see a fan relay. See if the black high speed wire is attached. Russ
found it and yes it is attached
Do you see a blue or red wire close to relay it may be plugged off. Russ
yes checked that they are not plugged off..
ok Russ my husband just said he adjusted the fan speed...guess we have to wait and see if that works...so frustrating when the temp is 69 but the humidity reads 73 ...cool but sticky lol...thanks for your help and have a great day :)
If youn have a blue wire that comes from fan motor that is med. Speed. Unplug high and plug in blue and see if it helps humidity level. Also if unit is not running long enough it will not remove the humidity. Russ
thanks for your help , we appreciate your knowledge :)