If unit is freezing up it a sign that unit has not enough air flow across air coil, it needs 400 cfm per ton
I am sorry, but i am not sure what this means? How do I get more air flow across the air coil? Where is the air coil? and what does 400 cfm mean? The builder put the pad that the air conditioner sits on in the corner so their are two outside walls that frame the airconditioner, should it be moved?
The inside unit is called the evaporator and it needs 400 cubic feet minute to be able to fuction properly if the builder short changed this it will freeze up
is there a particular air filter you recommend for maximum air flow over the coils. would having the air ducts blown help?
A pleated one will works the best either 1" thick or 2" thick if it will fit your unit. the duct work will work better clean but if its short its going to always be a problem
So sorry only one more question, who do I call to get the air duct length problem fixed or how do I fix it? I am a mom, so it's up to me to figure this out. Thank you for your time so very much.
Hire a good HVAC company to do a heat gain calc. that will determine the size unit needed to cool your house properly. Once you know the proper size then you design duct work to match the size unit you need. But in your case your duct work will have to be evaluted for proper size
Thank you very much, I will call to have the unit evaluated. You have been so helpful. Have a blessed day.