HVAC Questions? Ask an HVAC Expert for Answers ASAP
It would seem as though it is but remember the 100,000 is the input. you will multiply it by the efficiency (80 or 90 or 95%) to determine the output. Unless the house is older with poor insulation and you live in the northern parts, it will probably be oversized. Your furnace is a 90+ so your output is close to 90-95,000 btuhs. To give you some idea, I can heat my 2300 square foot home with a 75,000 btuh input but I live in the mid-atlantic. You want to be careful oversizing a condensing furnace. I would certainly recommend a load calculation be performed.