HVAC Questions? Ask an HVAC Expert for Answers ASAP
The two leads from outside go to C and Y1. The yellow from thermostat attaches to the Y1. The light blue is C Red goes to R. You should have a G terminal on furnace that the light green or G goes to. Russ
Did not get message.
So the yellow in the outside unit attaches to the Y1 in my thermostat harness, and the black outside unit wire attaches to light blue wire wire in my thermostat
Yellow to Y1 and black to C and just cap off the rest, right?
What color wires are on outside unit. Russ
I screwed up, they are yellow and black, not yellow and white as I first described them. Sorry.
Black wire goes to C. (Yellow to Y1 and Yellow from Tstat to Y1) Russ
And cap off the others then right?
Do you have G terminal on board. Russ
On the thermostat board? I will have to pull it apart to check that out.
Just go ahead and try the cooling the Y terminal should bring on fan. Russ
no G terminal, and I will try it out as you described. Thanks Russ!