HVAC Questions? Ask an HVAC Expert for Answers ASAP
Hello, In the blower door is a round viewing window...look in the window and tell me if you see a blinking red light
The window is the size of a 50 cent piece
it is blinking "13" now, but when I first restart the power it blinks "33".
Thank you!..do you mind a hands on test?
With the front door off...and straight ahead on the front wall is a "limit switch". Looks like this- [IMAGE][SRC][/SRC][ALT][/ALT][WIDTH]79.08163265306122[/WIDTH][HEIGHT]100[/HEIGHT][STYLE][/STYLE][/IMAGE]
I don't see that. Is it ehind the panel with the blinking light?
there is a kind of oval shaped object below the blower unit with two red wires running to it.
Ok, I was wrong ...for your unit it is a diferent switch....page 3 here - http://www.docs.hvacpartners.com/idc/groups/public/documents/techlit/58st-5pd.pdf
yes oval switch!
urn power off and tap that switch a couple times...turn power back on...wait 90 seconds and tell me what status light does
flashing light is on constant and flame comes on.
first it flashed "12" then the above happened.
Great, you just got it reset....what happens is if the unit overheats from dirty filter, badblower etc..it trips that switch. When it cools down it is supposed to reset..but yours got stuck. You should be all set now
thanks, XXXXX XXXXX if Lowes will take this thermostat back.
Thank you, XXXXX XXXXX have much money and I know you just saved us more than we could afford. Thank You so much. Dave