Hello. Welcome to JustAnswer.com. My name is XXXXX XXXXX I'll be happy to assist you today.
You will need to run 2 separate high voltage lines to that system (or one large one that splits in a 2 breaker outdoor box at the unit). The 30 amp rating is the unit without a heat kit. With the 10 kw kit installed, the minimum breaker sizes (remember, you will need 2 lines) are 45 amp and 52 amp, and the maximum is two 60 amp breakers.