Have HVAC Questions? Ask an HVAC Expert for Answers
Hello....were all 5 hooked up on old stat?
No , I removed the wires before I noticed the letter codes on the old thermostat.
Did I send you the right info
Ok...so were 4 wires hooked up?
I just need to know how many you think you took lose...
5 wires hooked up initially. I then removed all 5 wires and now need help with connecting those wires to the new stat.
Thank you....what do you have for heatng cooling equipment? Then there is a test to find wout what goes where
I have an oil fired heating system and Bryant AC cooling system
Ok....2 wire = red to rh and white to W. 3 wire = red to Rc, green to G and white to Y
Make sure you remove jumper between rc and rh
I wired it as suggested and it works! Thank you so much.