Have HVAC Questions? Ask an HVAC Expert for Answers
Hello. Welcome to JustAnswer.com. My name is XXXXX XXXXX I'll be happy to assist you today.
The function of each wire will vary depending on how the original contractor hooked them up to the original thermostat. Typically red will go to RC (with a jumper to RH), white will go to W, yellow will go to Y, and green will go to G. Since you don't have a green, most likely either the brown or blue goes to G.
Do you happen to know which wires went to which terminals on the old thermostat? Was there a wire connected to a C terminal on the old thermostat?
Okay, we need to be careful then. The C terminal is the 24v common terminal. If you connect the wire that was connected to C on the old stat to any of the terminals on the new stat you will blow a low voltage fuse (if equipped) or a transformer.
What we need to do is verify the wire designations at the indoor unit. Can you access the unit? Also, do you have gas or electric heat?