HVAC Questions? Ask an HVAC Expert for Answers ASAP
We have a Beckett Burner in Lockout and we need to reset. How?Optional Information:Make : BeckettModel : F35AD8C63
How many times have you pressed reset button?
Is unit in hard lockout at this point dong nothing when pressed?
If so, press and hold down button for 30 seconds to reset.
Also, has the unit ran out and you are bleeding the unit? Or do you have an ignition problem?
Regular lockout would be standard shutdown after no flame for trial period.
Example = Trial period is 30 seconds...flame doesnt light and trips reset. You can press reset and it will try again.
Hard lockout would be pressing reset with 3 shutdowns without flame.
Example = Trial period for 30 seconds was reset 3 times. At that point it goes into hard lockout requiring 30 second depression of reset button