I made the jump from R to W and the furnace came on. the wife is very happy. what next?
I dont know if you got my reply so iam sending it again. Its all good now. I used the wrong wires from a wrong set of wires to reassign at the furnace. there were 3 of the same wire bundles at the furnace. one to the sump pump on the floor and the other 2 coming down from the ceiling. I switched with the other set of wires and the system is working even with the thermostat installed. thank you for your help.
I replaced the blower motor and wheel couple month's ago. I had to use a generic motor mounting braket (had no rubber bushing, the metal arms bolted straight to the wheel housing) there is a humming or vibration when the motor is running. do you think adding rubber spacers between the bracket and housing will help.
when the furnace wasnt working this morning i noticed that the condensate pump was running non-stop. So i unplugged it from the wall outlet as i was checking the furnace. I just went back to the furnace to plug the condensate pump back up and found a puddle of water aroung the pump motor. I plugged the motor back and i can feel the motor running again. any action required? isnt condesation occur only with AC and not heat