Have HVAC Questions? Ask an HVAC Expert for Answers
rick, the circ pump is wired to 4 N/O & of course neutral. The house tstat is currently wired to TT on the operating control on the boiler, can a 2nd set of t-stat wires be added to it without interfering with anything? No line voltage jumpers to 5 or 6, only H to 3 on the taco sr501.