Have HVAC Questions? Ask an HVAC Expert for Answers
Held button down for 30 seconds. Light went off then came on once at end of 30 seconds and now stays off.
Yes but nothing happened.
What is T&T on primary control?
Don't you have 4wire connections on the box that has the reset button? If not give me the model number of the reset box.
There is a number on the box. I believe it is R718B.
Going back to basement to check, computer is two floors away.
Its R7184B and there are only two wires on this box.
Ok, here is a tech sheet on the control. This time hold down the button until the box flashes twice. Read this manual
Nothing is happening besides I am no longer on lock down light, now I am on no flame light off.
Here is the full troubleshooting manual
I am reading this, but this is not helping me much. I need some concrete advice on what to do, not tech manuals, unlike you I am not an HVAC expert.
Glad your'r getting back to me. I studied the tech manuals etc (I did have a lot of physics classes in high school and college) and after really reading them they no longer sounded Chinese to me. Turns out too much resetting or priming just floods the thing with oil, no wonder it would not light. So I did the only smart thing I could do, turn it off again over night and turn it back on in the morning. Got it working fine now, did not need any more priming either.
Thank you for the literature, I will keep them on hand for further reference, you saved me an expensive service call.
Excellent! If you had physics in college you are smarter than I am!
I thank you.