• 100% Satisfaction Guarantee
Rick Mather, HVAC Technician
Category: HVAC
Satisfied Customers: 3634
Experience:  35 years experience, HVAC
12095340
Rick Mather is online now

# My new furnace, a Ducane 95% efficent, was installed by a local

My new furnace, a Ducane 95% efficent, was installed by a local heating supply retailer. The Delta T readings were 126 duct temp, 72 input air temp, and -54 for a differential on his instrument. His comments were that my duct input and output capacity are ok because up to a 70 differential is allowed. I think the system is starving for return air. Can you enlighten me. Thank you very much. Paul
What size duct on return do you have and what is the drop down to return plenham
Customer: replied 6 years ago.
This is a replacement propane furnace to one that was installed in 1992 before electric heat became so expensive. Conequently there is no return duct and the heated air returns from the whole house of 1400 sq ft down thru an open stairway to the cellar. The return at the furnace is thru the base of the furnace, placed on four cement blocks, leaving an area on each side of 7.5 x 14.5 in. I output plenham is attached to the original duct work of 18 X 20 in. Please explain the use of Delta T in this analysis. Thanks
Delta Temperature is the difference between the leaving air and the return temperatures which really does not always tell the whole story. it would be better to take transverse of duct for the CFM that is going thru unit with manometer. This will tell the exact amount of air going across the heat exchanger
Customer: replied 6 years ago.
Can't you make a judgement by the temps I gave you about duct effiency? I know that manometer readings will tell for sure but it still is all about heat transfer temps? paul
Well with some type of chart that would state what type of temperature difference to expect I cannot make a judgement on your performance on that unit but a 54 degree rise does not sound that bad
Customer: replied 6 years ago.
My installer said the limit was 70.. is this correct for delta T?
Sounds reasonable
Rick Mather, HVAC Technician
Category: HVAC
Satisfied Customers: 3634
Experience: 35 years experience, HVAC
Customer: replied 6 years ago.
Rick .. I think I was looking for a more diffinitive discription of Delta T as it relates to duct size and furnace efficiency. Paul
I told you unless the manufacturer has a chart that gives comparison it would be meaningless information. It has to measure against a known value such as a chart.or gragh

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

### What Customers are Saying:

• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
< Previous | Next >
• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
• Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help. Mary C. Freshfield, Liverpool, UK
• This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!! Alex Los Angeles, CA
• Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult. GP Hesperia, CA
• I couldn't be more satisfied! This is the site I will always come to when I need a second opinion. Justin Kernersville, NC
• Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around. Esther Woodstock, NY
• Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know. Robin Elkton, Maryland

• ### Phil

#### Satisfied Customers:

5389
Retired HVAC/ Electrical & Boiler contractor. Industrial
< Last | Next >

### Phil

#### Satisfied Customers:

5389
Retired HVAC/ Electrical & Boiler contractor. Industrial

### gotoman for ac

#### Satisfied Customers:

4999
51 years of experience install design and repair of all makes and models of AC

### Rick Mather

#### Satisfied Customers:

3133
35 years experience, HVAC

### Matthew

#### Satisfied Customers:

2014
14 years experience in the HVAC field of service, installation, Manual J & D calculations

### Kenton Guidry

#### Satisfied Customers:

963
12 years install/service experience.

### Rick Ridley

#### Satisfied Customers:

871
Retired But have had 30 years on the tools, Ex CORGI

### Tom

#### Satisfied Customers:

770
16+yrs HVAC/R service. Residential Commerical Industrial