What is the brand and the model of your new digital thermostat. I can get the manual on it and tell you how to check the anticipator setting.
Look in your manual and look under swing andthen look under calibration. Do what it says and let me know what reading you get
That will be fine. I have a dinner appointment with a customer tonight so it will be around 9 or 10 pm CST before I can get back with you unless you post between 5 and 5 pm
have a good day
Check the temperature rise across the furnace. Put a thermometer in the return duct and take a reading, then put the same thermometer in the supply duct and take a reading. Subtract the return reading from the supply reading and you get the rise across the furnace. The rise should be between 30 to 70 degrees. Tell me what the rise is.
Also, check the calibration of the thermostat in your manual. Do you see a box on the back wall of the compartment where the gas valve and burners are. If you do, unplug the furnace and take the cover off. You will see a round dial face. There are 3 setpoints on that dial, the first one is "fan off", the second is "fan on", the third is "high limit". Tell me what each setpoint is.
Tell me about the door you remove to make the furnace run correctly and not shut down. Is this the door on the front of the furnace where the controls are located?
Hi! I am Al. I apologize for the confusion that you have experienced on JA. I have 35.5 years of experience in the HVAC field. I guarantee you that I can give you a solution to the problem that you are experiencing. However, I can understand how difficult it must be to differentiate the correct advise when one of JA experts is interrupting in between yours and I (AL) , communication.
I will check with my tech support team once I have your equipment information. Beware of anyone that post another answer or question concerning your issue. I will do my best to serve you with the most equitable solution to your problem. Your satisfaction is the main goal here. Give me a chance and I will provide you with a quality solution
To remedy the confusion you have had to deal with I will continue to work with you until you and i achieve a solution to your problem and I will do it for free. Your satisfaction is my goal. If you come to JA an experience unprofessional activity I will guarantee you a solution for free.
With all due respect, the electrifier is a mechanical inspector. I am a professional HVAC service technician with 35 years of technical troubleshooting experience. At this point to assure that you get a correct solution I will work with you until this issue is resolved for free. I want your problem to have a solution without you having to deal with confrontational issues from within the JA experts. So rest at ease. I guarantee you a solution with no charge. You can email me at xxxxxxxx if need be. YOUR SATISFACTION IS THE GOAL.