HVAC Questions? Ask an HVAC Expert for Answers ASAP
Hi,still not working.What i have done so far is I went to the source(ie) Oil Tank.Took filter,and cleaned,next I followed the Oil pipe to where it enters the Boiler.I tried bleeding this,and no oil came out,so i took of the pipe,where it enters the burner,and Oil started to seep out.After connecting this back up,I loosened the bleed nut,and tryed again,still not fire up,but after a few seconds,I tryed again,but this time I left the bleed nut loose,the fuel started to gush out,and then i tightened the bleed nut up,and tryed again.Still no joy.The only thing that i can think of what caused this problem,is dirt,that was picked up when the tank ran dry,and blocked the system.I think the next thing that i need to check,would be the jet.Or do you think It may be something else.And lastly,would ti be hard to change the jet,if that is what you think may be the cause.
Sorry for this being longwinded,but i am trying to give you as much information as I can.
you need to verify that the pump is actually pumping. disconnect the small oil line going to the nozzle assy. & put it in a clear bottle and hit the reset. i use a pressure guage for this but i doubt you've got one. if it pumps good,cut it off ,pull the nozzle assy. & replace nozzle. be careful not to crack the porcelains or move electrode tip settings. be careful when it starts cause it sounds like you have seriously loaded it with raw fuel.if it fires and rumbles, kill the power and dont re-light it until the flames are totally out. if it does'nt light after that your transformer is probably weak. settings on electrodes are as follows:
1 half inch up above center hole in nozzle
1 eighth out in front of nozzle
1 eighth gap between electrodes
Thank you for the very informative,step by step information.I done all this the morning,and after replacing the nozzel,and checking the settings,i had to clean the electrodes,and reset the gap,to your settings.It runs perfect now.I got the boiler fully serviced,2 months before i stopped using it,and the thermastat was set at 70c,and with this you could put and keep your hands on the rads,now i have it set to 60c,and now it you could not keep your hands on the rads.And also while running now,it is alot quiter,than before.I am going to except this,but after reading,if this sounds,wrong,please let me know. my e-mail is, XXXXX@XXXXXX.XXX.
Its a central heating oil boiler,that heats the water,for the hot tank,and the radiators It seems to be running very quiet,and producing better heat,compared to after it had its full service.Have had it running three times too day on 2 hour intervals,due to it snowing, and every thing seems ok,if not better than before,thanks to yourself.
Thanks for all your help,and very informative information.
Have a Happy, Christmas& a Happy New Year.