Electrical Questions? Ask an Electrician Online.
Hi, I'm Mike G and I'll be assisting you. Please give me the count and colors of the wires in the box.
Depending on whether you want the switched load GFCI protected or not. Protected, put the white wire on the load terminal, Unprotected, put it on the Line termination. The wires from the device switch, connect one to the Line or Load hot termination and the other wire to the black switched wire.