Electrical Questions? Ask an Electrician Online.
What size circuit do you have there?
What is the load for the well?
What are the number of wires on the existing feeder?
How are is the pool from the proposed panel?
You are short 1 wire and the wire size is insufficiant for installing a sub panel. You need to run a new circuit or feeder.
You don't understand me. The size of the wire to the well was no doubt sized for Tyne well only. It not only being to small it is short 1 wire. Both make it advisable to run a new feeder if you want a sub panel or you can only run a new circuit for the pool. From the way you asked the question, I assume that you don't know the other requirements for a pool wiring. Equipotential bonding and distances for outlets and disconnects. Pool wiring has to be right all the time. Any thing missed will expose you to a shock hazard.