Electrical Questions? Ask an Electrician Online.
Hi, I'm Mike G and I'll be assisting you. Please tell me the number and colors of the wires in the ceiling box and colors connected to the fixture. Also I need to know the wire colors on the switch.
:Are you saying that there are 3 terminations on the switch and that all wires in the ceiling are connected by color with none free for connection to the fixture? Do you have a 2 wire voltage tester?
A picture of both boxes would help.
Can't be correct if the wires in the ceiling are all connected black to black....white to white. There has to be one wire switched. Do you have a 2 wire voltage tester?
Disconnect the black wires at the ceiling, find which one is a hot, one at a time connect a black to it and test at the switch to identify the wire from the ceiling. The white wire paired with that black should be connected to the hot with all the other blacks. The identified black and the white wires connection is where to connect the fixture.
No, the white to the switch with the blacks. Black to switch tofixture. Remaining whites to fixture.
It'paired with theblack you identified. When connected to the hot it will have voltage at the switch.
Anytime you see a white connected to a black it is going to a switch. That's the norm.____
Very good, you're welcome.