Electrical Questions? Ask an Electrician Online.
Hey Steve. Code requires a demand factor for the 4 units at 100A have a 45% factor which makes a 200A service. See Art 220.84
I can call tomorrow if that works for you.
To avoid the phone charges we can continue via the site.. Do you have a code book?
Art 220.84 Table is all that is needed for calculating the demand factor of the service size.