Electrical Questions? Ask an Electrician Online.
Hello my name is ***** ***** I will be happy to assist you. Do you know if your bathroom has a GFCI receptacle? It may be fed off the load side of the receptacle, or perhaps from a GFCI receptacle from another washroom. That may be tripped
Ok, so power to the plug and it is working fine. But no power at the switch. How many wires in the switch box?
And no power on any of them? what colors and what is connected?
What do you have for a tester? Are there no whites in the box?
And for sure all the breakers are on? Sometimes they are tripped but they still look like they are on
How many wires in the ceiling box? Are there any other lights or plugs in the area that are also not on?
white and black?
ok then that black goes to your switch and the white is connected to another white in the box?
so the 12-2 runs from the switch box, to the ceiling light. 12-3 brings power into the switch box. you will have to open up some other boxes in the area, to try and find the other end of that 12-3 and see if that is where the power drops out