Electrical Questions? Ask an Electrician Online.
Hi, I'm Mike G and I'll be assisting you. Test each black to neutral and then to ground. Let me know the readings. Only on should be hot with the GFCI tripped.
You have a bad neutral connection on the feed. You'll need to check connection ahead of the GFCI. It won't reset if you have a bad neutral connection.