Electrical Questions? Ask an Electrician Online.
I'm here, go ahead.
Your meter setting is at 4 o'clock on the dial 300ACV. The needle should go around half way and the scale used is the one marked 300V. If it would be easier you could authorize a phone call.
I'm sorry for the delay, we're having a problem with the site. I'll get to you as soon as possible. Hang in there.
The hot pair go to the receptacle, black to gold screw, white to silver screw.
Connect the white to the socket to the receptacle silver screw.
Connect the white to switch to gold screw on receptacle.
Connect short black jumper wire from gold receptacle screw to switch.
Connect black from socket to switch.
Connect all grounds together and to both devices.
As I understood you, the switch controlled the socket. If not, what is the socket and is there a light somewhere?
Did you refer to the receptacle as a socket. If so, I'll need to amend the directions.
Black and white from the feed pair to receptacle.
Black jumper wire receptacle to switch -gold screw.
White from light to receptacle silver screw.
Black from light to switch.
In a fan the whites are connected together and if only one switch the other wires are connected together. I thought you were doing a wall box.
No problem. Stand by.
Hello, what exactly are you trying to wire? and what box are all the wires in that you are working on?
Ok, so you are just replacing an existing light with a new fan? All the wiring is in the ceiling box? You have an existing switch already?