Electrical Questions? Ask an Electrician Online.
Hi, I'm Mike G and I'll be glad to assist you. Tell me how many wires and their colors on the new device. Better yet, upload a picture if you can.
OK, connect the device as follows.
On one side there will be either black or gold screws with a bridge between them. Connect the black feed wire there.
On the other side there is a gold and a silver screw. Connect the black wire to the light to the gold screw and the white neutral feed to the silver screw.
The black and neutral feed wires should be connected to the other switches and neutrals as they where when you first opened the box.
Is the bridge between the feed side intact? Does the outlet work?
Does the outlet work?
Was the outlet originally there wired indepentant of the other devices?
It should be pigtailed to the other whites.
All whites connect together with a pigtail to the silver screw of the receptacle.
Not necessary, it would be redundant unless you brought the feed to the box bypassing the existing GFCI.
We're happy to hear that.