Welcome. My name is XXXXX XXXXX would be glad to assist.
Are all of the breakers in the panel the QT style, with 2 mini breakers per 1" space?
Do you see the name brand on the panel cover?
Do have at least one unused 1" slot or a couple standard 1" breakers that are not the QT style?
Just reply when you return and we can work from that point forward, thanks
Hi Tommy. It is a Siemens. All of the breakers in the panel are, indeed, the QT style. There are a still few open 1" slots without a breaker, they aren't even punched out yet. Some of the slots have 2-mini breakers, others have 1" breakers with 2 poles. The one I am wanting to replace is a mini-breaker, in the bottom half of of on the 1" slots. The top mini breaker in that slot services another area of my home. Hope this helps !
Ok, thanks for the information. What you would need to do in your case, since they only make GFCI breakers in the 1" width. -----Purchase a standard size GFCI Siemens breaker-----CLICK HERE to see it at HD----You will disconnect the black wire from the breaker that controls that circuit you want to protect with the GFCI. ---------After disconnecting the black wire, you then trace the wire back to the cable that it is part of.-------- Once you find the cable it comes out of, get the white wire in that same cable -----and follow it to the neutral bar that it connects to and remove it from that bar. ----------You will then install a standard size GFCI breaker in one of the unused slots. ------Connect the black wire to the GFCI, --------connect the white wire to the GFCI (it is marked with white color or is silver). --------Then there is a pigtail wire that is made into the breaker, you take it and connect to the neutral bar where you disconnect the white that was put on the breaker.
Let me know if any other is needed
Excellent instructions ! That listing says 1-1/2". You sure it will fit ?
They only take up one space in the panel. Guess I use the wrong terminology with the 1" space. Her is the specs on the QT breakers themselves-----These space saver duplex breakers combine twoindependent 1/2" breaker poles in a common unit.This unit plugs into one load center stab andrequires one panel space. HACR rated.----------------The little breakers are 1" but add the space in the middle and sides and it is wider.
Both take up one breaker space each.
Thanx Tommy - have a good one !