• 100% Satisfaction Guarantee
Steve G., Electrical Engineer
Category: Electrical
Satisfied Customers: 17711
Experience:  Spent 20 years as an Electrical Engineer, designing electrical plans and specifications.
329447
Steve G. is online now

# I have a double wide trailer with the main panel outside and

I have a double wide trailer with the main panel outside and another in the house. It is 200amps going to the box outside. From there, there is a breaker for the well pump and the A/C.
What I need to do is get down to 100 amps on the outside panel, then to 30 amps. What I am doing is putting a 30 amp plug for my RV.
Can I just put a 100 amp breaker in the box then go from the 100amp to the 30amp?
Hello there and welcome to Just Answer. My name is XXXXX XXXXX I will be assisting you today. I am an engineer with over 30 years of electrical and electronic training, repair and installation experience. I will try and answer your question accurately and precisely so that we can get you on your way.

Now..just so I understand, you have a 200A breaker in a panel outside? If so, is there space for double pole breaker?

Please let me know so that we can continue.

Regards
Steve
Customer: replied 2 years ago.

yes I have 6 open slots

Ok, so why not put a double pole 30A breaker in that panel and take that to your RV connection box?

Or am I missing something?

Please let me know so that we can continue.

Regards
Steve
Customer: replied 2 years ago.

because 200a will blow everything in the RV it needs 115v 30a

Ok, you are getting confused between voltage and current.

A device (like your RV) draws the current that it requires and no more. You can put a 20A breaker in an 800A panel and you will draw no more than 20A. You could put a 20A breaker in a 1600A panel and it would draw no more than 20A. You get the idea?

Now, are you sure that you need 115V 30A? That is not a usual configuration. It is more likely that you need a 120/240V 30A feed.

In this case you would use a double pole 30A breaker in the panel and take two hots a neutral and a ground to your RV connection box.

Tell me, how many pins are on that RV connection plug?

Please let me know so that we can continue.

Regards
Steve
Customer: replied 2 years ago.

it has 3 so why cant I put a 100a in and then go from there to 30a

Because that is not how electrical design works. If you want to pay for a 100A breaker and wiring capable of carrying 100A, you would need to terminate that at another panel and then put a 30A breaker in there. This is all costly and unnecessary.

There is no reason why you can't put a 30A breaker in the panel you have now. Then you only have to pay for 30A worth of wiring, not 100A.

You will need a 30A single pole breaker that will fit your existing panel If the length of run is not excessive (over 50 feet) you can use #10 wiring.

Does that make sense?

Let me know. I'll be here.

Steve
Customer: replied 2 years ago.

just so I am sure.......................just put a 30a breaker in and hook up to the plug. 200a will not go through that 30a just 30a?

Exactly.

Again, you are confusing voltage and current. Current is determined by the device that is plugged in - your RV. And breakers are safety devices that limit the current. So again, if I had a 1600amp panel and used 20A breaker in it feeding a light circuit (for example), the light circuit would not draw 1600A. It would draw no more than 20A because if it did, the breaker would trip.

So, find out who makes your 200A panel and get a single pole 30A breaker for it. Take a #10 hot, neutral and #12 ground to your receptacle box and you are good. No more than 30A will flow through that circuit because of the breaker. And no more than 120V because you are using a single pole breaker.

I'll be here if you need further help with this issue. Please let me know.

Regards
Steve
Customer: replied 2 years ago.

Thank you very much Steve you were a big help

Don't mention it. If you need more help, I'll be here.

Here are the rating options. Please pick a good one so that I may be credited with helping you today.

Good luck.

Steve
Steve G., Electrical Engineer
Category: Electrical
Satisfied Customers: 17711
Experience: Spent 20 years as an Electrical Engineer, designing electrical plans and specifications.

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

### What Customers are Saying:

• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
< Previous | Next >
• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
• Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help. Mary C. Freshfield, Liverpool, UK
• This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!! Alex Los Angeles, CA
• Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult. GP Hesperia, CA
• I couldn't be more satisfied! This is the site I will always come to when I need a second opinion. Justin Kernersville, NC
• Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around. Esther Woodstock, NY
• Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know. Robin Elkton, Maryland

• ### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer
< Last | Next >

### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

### Jason

#### Satisfied Customers:

3871
Over 20 years of experience in all types of installations, troubleshooting, and repairs.

### Mike G.

#### Satisfied Customers:

6511
Proven Professional 46 years Experience

3264

### Kevin

#### Satisfied Customers:

2371
29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector

### electrifier

#### Satisfied Customers:

1458
Electrical contractor and electrical inspector for over 24 years with phone and networking expertise