Welcome. My name is XXXXX XXXXX would be glad to assist.Could you give a little more detail, please?You have this wiring in place or you are wanting to run cables and make an addition?You state 3 ways and another switch, which switches will control the fan?Will the fan have a light also?Thanks
I remodeling a hallway so we'll call it new construction. Ive ran 14/2 from the breaker to the first 3 way switch then 14/3 to the next switch then i planned on running 14/3 to the fan/with lights. However id like to control the fan itself on a separate switch then the lights. I only want one switch for the fan itself but 2 (on each end of the hallway) to control the lights.
All is accurate except the double gang has the 14/2 (power) coming into it.
Can i just splice the power to both switches in the double gang box and run an additional 14/2 from the single switch to the ceiling fan to operate the fan alone?
In other words the ceiling fan would have a 14/3 (control lights at two different locations) and an additional 14/2 running into it to control just the fan?
Seems odd that 2 powers (14/2 and a 14/3) run into the same box?
It looks good. Just to be clear though. 14/2 into the double gang. 14/3 to the second 3way switch. and 14/3 from the double gang to ceiling fan?