Electrical Questions? Ask an Electrician Online.
Hello. Welcome to Just Answer.
There are a few things you should check in this situation...
Make sure the neutral wire for that circuit is tight in the breaker panel.
Then, open the outlets and check to see if the wires are connected via the small push-in holes on the back.
If they are, I would redo the connections using the screws on the sides of the outlets.
If you find any splices in any of the outlet boxes, check them to make sure no wires will pull out.
ok i will try that does there need to be a ground rod grounded to the box outside I cant find one
If this is your main panel for the house, there should be a ground rod outside.
there is a pices og rebar sticking out of the foundation with a wire clamped to it was all i can find
Rebar should be grounded, and it may be, if it's in contact with soil.
ok thank you i will check every thin you said