Fuse blows when turning light switch to off after changed from dimmer switch to regular light switch and changing light fixture. I capped off red in light switch and light fixture. I connected all black to black wires and all white to white. I don't see a ground wire. There are 4 outlets involved that did not work when red wire was connected to light fixture and switch in place of black and black wires were capped off. Outlets work with red wire capped yet fuse blows when light switch turned to off.
The new light switch has 2 gold screws on one side and 1 green on the other.
The outlets have only black and white wires.
Switch box has 2 black, 2 white, 1 red.
Fixture has 2 black, 2 white, 1 red
No. The red wire does not leave the fixture. It was connecteted to thblack wire on the fixture itself. That's when the switch and 2 outlets on the same wall worked, yet the outlets on the other 3 walls didn't work. The work now with red wire capped off yet now the fuse blows when I flip the switch off to the fixture.
I did have the red and white hooked to the standard switch that has 2 copper or gold screws on only 1 side with 1 green ground on the other. I originally had all the black capped off as mentioned earlier.
I had removed the original dimmer switch and went to the standard switch and changed the fixture with a newer one. This is when the outlets stopped working.
I am going to just place a switch that has a black screw and 2 screws for the traveler wires. I will connect the black hot wire to the black screw and the red and white to the other 2 screws. It appears the black wires must be used in order to keep power to the outlets.
I was just wondering if I could connect the red wire in the fixture to the black wires. There is also 3 black wires and 3 white wires and only 1 red wire in the fixture instead of 2-2-1 as mentioned earlier
or should the white wire and red wire be taped together in the fixture since they are the traveler wires?
It worked. Thank you. You helped me a ton and saved me money.