Hello, my name is XXXXX XXXXX I'm here to answer any of your electrical questions.
Can you tell me what reading you're getting when you test from hot to ground, then hot to neutral please.
hot to neu 93 ac
hot to gnd 25 ac
Are you getting this throughout the whole house, or just one circuit?
just one circuit
What about at the breaker? Are you getting the same readings there?
Sounds like you have a loose neutral. Can you follow which neutral wire is paired with that hot wire, and see if it's nice nd tight?
this would be in the main box correct
ok I will try that I would make sense as that circuit had a history of flickering lights
That is also a symptom of a loose neutral. Let me know what you find.
ok going to check now
no all is good in the box had 120 vac coming out of box on the circuit it must be at the first outlet
Exactly. Since you have the circuit identified it should be pretty easy to find. It will probably be a outlet with a stab in the back connection. These normally fail eventually.
ok ill half split the circuit till I fin it shouldn't take long thanks