• 100% Satisfaction Guarantee
Category: Electrical
Satisfied Customers: 2402
Experience:  29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector
71008832
Kevin is online now

# My house (in rural central Indiana) has 200 amp service. I

### Resolved Question:

My house (in rural central Indiana) has 200 amp service. I want to run a 100 amp, 220 volt, branch underground service to a barn located 170 feet away. What size/type of cable should be used, should it be in a pvc conduit, and how deep should it be buried?
Submitted: 2 years ago.
Category: Electrical
Expert:  Kevin replied 2 years ago.

Hello Terry.........my name is XXXXX XXXXX I will be happy to assist you with your electrical question. My goal is to exceed your expectations on Just Answer!

1) The voltage drop calculation for a 100 amp sub-panel, 240 volts at a distance of 170 feet results in 1/0 Stranded Aluminum which provides a 2.4 voltage drop or 2 AWG stranded copper which results in a 2.7 voltage drop. Due to the distance, Aluminum wire will be more cost effective than copper conductors. Code requires the voltage drop to be less than 3 volts.

2) Since a sub-panel, the feeder circuit leaving from your 200 amp main panel needs to be a 4 wire circuit, ie , 2 hots, 1 neutral and 1 equipment grounding conductor.

The 2 hots and 1 neutral can be sized as 1/0 Aluminum and the equipment ground size is a minimum of 6 AWG Stranded Aluminum.

3) If using PVC conduit, you can use Sch 40 gray electrical PVC, 2 inch diameter. For the conduit fill ratio, code requires a minimum size of 1 1/2" inch diameter conduit, however I would suggest using 2 inch diameter as this will make pulling the conductors much easier. The wires will need to be rated as type THWN insulation for wet conditions. Or you can use Underground Feeder (UF) 4 conductor cable as a direct burial. I always recommend using conduit for underground since you only want to trench this one time.

4) You will need space in the main panel to accommodate a 100 amp double pole breaker. The main panel and the sub-panel will both require an equipment grounding bar. Located at both the main panel and the sub-panel, the equipment grounding conductor lands on an equipment ground bar and never on the neutral bus bars. At the barn, you will require a minimum of (1) one 8 foot ground rod.

5) If using PVC, burial depth is a minimum of 18 inches. If using UF cable, minimum depth is 24 inches.

6) The sub-panel in the barn will need to be a main breaker type of panel and not a main lug panel. At the sub, the neutral wire must remain isolated from the panel metal enclosure. This means, do not install the green bonding screw or the copper main bonding jumper at the sub neutral bus bar. The neutral always remains floating in any sub-panel. The grounding electrode conductor to the ground rod can be sized as either 8 AWG or 6 AWG Stranded Aluminum. Depending upon your soil conditions, you may require 2 ground rods installed a minimum of 6 feet apart. Best to ask your local electrical inspector for soil grounding conditions in your area.

Hope this helps.........If you have any additional questions, let me know and I'll be glad to answer them for you.

Otherwise, don't forget to rate me before you log Off.

The next time you have an electrical question, you can also request for me at:http://www.justanswer.com/home-improvement/expert-your-electrician
..........Thanks..............Kevin!

Category: Electrical
Satisfied Customers: 2402
Experience: 29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector
Expert:  Kevin replied 2 years ago.

Terry...... Thank you for the excellent service rating as well as the bonus......much appreciated!

If you have any other questions, just let me know.

Take care and have a great day............Thanks..............Kevin!

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

### What Customers are Saying:

• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
< Previous | Next >
• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
• Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help. Mary C. Freshfield, Liverpool, UK
• This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!! Alex Los Angeles, CA
• Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult. GP Hesperia, CA
• I couldn't be more satisfied! This is the site I will always come to when I need a second opinion. Justin Kernersville, NC
• Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around. Esther Woodstock, NY
• Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know. Robin Elkton, Maryland

• ### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer
< Last | Next >

### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

### Jason

#### Satisfied Customers:

3871
Over 20 years of experience in all types of installations, troubleshooting, and repairs.

### Mike G.

#### Satisfied Customers:

6511
Proven Professional 46 years Experience

3264

### Kevin

#### Satisfied Customers:

2371
29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector

### electrifier

#### Satisfied Customers:

1458
Electrical contractor and electrical inspector for over 24 years with phone and networking expertise