How JustAnswer Works:
• Ask an Expert
• Get a Professional Answer
• 100% Satisfaction Guarantee
Ask Kevin Your Own Question
Kevin, Licensed Electrician
Category: Electrical
Satisfied Customers: 2398
Experience:  29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector
71008832
Type Your Electrical Question Here...
Kevin is online now

# i need to lay an underground line for my shed a distance of

### Resolved Question:

i need to lay an underground line for my shed a distance of 250m away was wondering what size cable i should use
Submitted: 2 years ago.
Category: Electrical
Expert:  Kevin replied 2 years ago.

Hello.....my name is XXXXX XXXXX I will be happy to assist you with your electrical question. My goal is to exceed your expectations on Just Answer!

1) Can you provide me with the voltage and the amperage of the LOAD?

2) Will you be using aluminum or copper cable?

Customer: replied 2 years ago.

240 v as for amprage not sure will need to run a 200 amp welder as well as lights grinders etc

Expert:  Kevin replied 2 years ago.

1) Thanks for the replies Ian

2) I have calculated the voltage drop using a 240 VAC Single Phase line voltage ,a 200 amp LOAD and 250 meters (820 feet) as follows:

2A) Using aluminum conductors, this results in a 2.8% voltage drop or 6.6 volts using 900kcm conductors.

2B) Using copper conductors, this results in a 2.8% voltage drop or 6.8 volts using 600kcm conductors

3) It is recommended to maintain the voltage drop less than 3%.

4) Due to the length of the cable run and a high amperage load of 200 amps, the use of aluminum conductors will be more cost efficient versus copper conductors.

Hope this helps.........If you have any additional questions, let me know and I'll be glad to answer them for you.

Otherwise, don't forget to rate me before you log Off.

The next time you have an electrical question, you can also request for me at: http://www.justanswer.com/home-improvement/expert-your-electrician
..........Thanks..............Kevin!

Expert:  Kevin replied 2 years ago.

Ian..... I see that you are in Australia and your wire sizes and voltage tolerances are different than what we use in the US. I will opt out of the question and another expert will be able to provide you with your cable sizes.

Kevin, Licensed Electrician
Category: Electrical
Satisfied Customers: 2398
Experience: 29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector
Kevin and other Electrical Specialists are ready to help you

### JustAnswer in the News:

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
JustAnswer.com...has seen a spike since October in legal questions from readers about layoffs, unemployment and severance.
Web sites like justanswer.com/legal
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

### What Customers are Saying:

• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
< Previous | Next >
• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
• Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help. Mary C. Freshfield, Liverpool, UK
• This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!! Alex Los Angeles, CA
• Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult. GP Hesperia, CA
• I couldn't be more satisfied! This is the site I will always come to when I need a second opinion. Justin Kernersville, NC
• Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around. Esther Woodstock, NY
• Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know. Robin Elkton, Maryland

• ### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer
< Last | Next >
• http://ww2.justanswer.com/uploads/mikepettinato/2009-9-4_41145_DSC005132.jpg Mike's Avatar

### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer
• http://ww2.justanswer.com/uploads/WI/WireitUp/2012-6-17_18212_Photo00006.64x64.jpg Jason's Avatar

### Jason

#### Satisfied Customers:

3871
Over 20 years of experience in all types of installations, troubleshooting, and repairs.
• http://ww2.justanswer.com/uploads/MI/MikeG2010/2012-6-7_192640_IMG01612.64x64.jpg Mike G.'s Avatar

### Mike G.

#### Satisfied Customers:

6511
Proven Professional 46 years Experience
• http://ww2.justanswer.com/uploads/AS/AssuredElectrical/2011-9-13_221243_me.64x64.gif AssuredElectrical's Avatar

### AssuredElectrical

#### Satisfied Customers:

3264
Contractor-42+ Years in the ElectricalTrade
• http://ww2.justanswer.com/uploads/UR/urelectrician/2012-9-28_223652_JustAnswerPic.64x64.jpg Kevin's Avatar

### Kevin

#### Satisfied Customers:

2371
29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector
• http://ww2.justanswer.com/uploads/electrifier/2008-12-16_200429_headbob1.jpg electrifier's Avatar

### electrifier

#### Satisfied Customers:

1458
Electrical contractor and electrical inspector for over 24 years with phone and networking expertise
• http://ww2.justanswer.com/uploads/rich03dungo/2010-3-17_101556_tshirt2.jpg Rich's Avatar

### Rich

#### Satisfied Customers:

1115
Over 35 years residential, commercial, industrial wiring, install, troubleshoot, service, maintain