Helloo .. Rich here .. lets see if we can help you with this .. can you tell me what size wires these are in the box .. or matbe read the size on the jacket of the cable
It is in the crawlspace under the house, a big hassle to get to. I took a picture though which I'll try to paste in here.
I just took a photo of the other end of the wires where they come out at the garage's panel.
There was a lot of printing on the wires but no clear statement of what the wire gauge is.
Thanks for taking the time for this Rich. I really want to avoid a fire, but I also want to have reasonable expectations for what the electrician's work should look like.
OK .. well it does look like he could have used a larger box for in the crawl space ... good news is that all the connection look really good .. they look like they are covered well with insulating tape and electrical tape .. I think that by the code if that conduit is 3/4 inch then the box is code ... yes it looks tight ..