Welcome. My name is XXXXX XXXXX would be glad to assist.
Hello, Paul here
what is the coil voltage of the relay? What is the voltage on the lights?
both r 120
120 coil and lights are also 120 volts?\
standard photo cell, black, red and white wires?
give me just a min for the initial diagram
Look it over and see if anything needs to be different? Used the same power supply for the photocell and lights to keep it simple
Turn your contact to the NO , Normally Open position
Are all the neutrals tied in together
No need to use the neutral through a relay
If you were 240 v on the lights, then use the other side of the relay and second set of contacts
diagram make sense and good for you?
yes it does,,,thank u
You are very welcome. Glad to be of service.
If needed, I will call again
Ok, sounds great