• 100% Satisfaction Guarantee
Jason, Service Technician
Category: Electrical
Satisfied Customers: 4220
Experience:  Over 20 years of experience in all types of installations, troubleshooting, and repairs.
9920183
Jason is online now

# 7.5 kw heat at 208 volt 3 phase equals how many amps

### Resolved Question:

7.5 kw heat at 208 volt 3 phase equals how many amps
Submitted: 3 years ago.
Category: Electrical
Expert:  Jason replied 3 years ago.

Jason :

Jason :

This calculates to about 36 amps.

Jason :

That being the case, I would feed it with a 50 amp breaker, and #6 copper wire.

Jason :

If you are using THHN stranded building wire, it can be #8/

Customer:

can you provide the formula that you used

Jason :

Sure. Volts X Amps = Watts. We know the wattage is 7500, and the voltage is 208. So, just divide the watts by the volts, 7500/208 to arrive at 36 amps.

Customer:

watts divided by volts--x 1.732 equals amps correct ??this is 3 phase

Customer:

are u there

Jason :

Thank you for your patience. I'm referencing my materials, as it's been a while since I had to determine when to use the 1.73 rule.

Jason :

Yes, you are correct. I was mistaken. 36 X 1.73 = 62.28. That would be a 70 amp breaker and #4 copper wire.

Customer:

ok---explain this:

Customer:

7500 watts at 240 volt SINGLE phase is 31.25 amps (watts divided by volts)---7500 watts / 208 volts=36.06 times 1.732 is= 62.46 amps----shouldn't the amperage on 3 phase be lower than single phase ???

Jason :

Now that I look at it again, I believe we are both misapplying the formula.

Customer:

what am i doing wrong ?

Jason :

We don't need to multiply the original amperage I arrived at by 1.73.

Jason :

That is to find watts.

Jason :

Wire is sized on amperage, not wattage.

Customer:

a 7.5 kw heater at 208 3 phase

Customer:

7.5 is 7500 watts

Jason :

Yes

Customer:

so only 7500 divided by 208 ??

Jason :

Yes.

Customer:

ok--thanks

Jason :

I apologize for being rusty, it's been a while since I've had to use the 1.73 rule.

Customer:

gues im done--nite

Jason :

If you don't mind standing by for a moment...

Jason :

I just found a site that explains it very well.

Customer:

so i just close this web site now ?

Jason :

I'll post a link after I view it.

Customer:

ok--go i go now ?? dinner is waiting

Jason :

You can go and come back later. No problem.

Jason, Service Technician
Category: Electrical
Satisfied Customers: 4220
Experience: Over 20 years of experience in all types of installations, troubleshooting, and repairs.
Expert:  Jason replied 3 years ago.
OK, here's a site that explains it well...

So, according to this info, you need to first multiply your voltage by 1.73. That comes out to about 360 volts. Then, divide your wattage by that number, which comes out to just over 20 amps.

So, I would run #10 wire, and put this on a 30 amp breaker.

Ask-a-doc Web sites: If you've got a quick question, you can try to get an answer from sites that say they have various specialists on hand to give quick answers... Justanswer.com.
...leave nothing to chance.
Traffic on JustAnswer rose 14 percent...and had nearly 400,000 page views in 30 days...inquiries related to stress, high blood pressure, drinking and heart pain jumped 33 percent.
Tory Johnson, GMA Workplace Contributor, discusses work-from-home jobs, such as JustAnswer in which verified Experts answer people’s questions.
I will tell you that...the things you have to go through to be an Expert are quite rigorous.

### What Customers are Saying:

• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
< Previous | Next >
• You did one super job of explaining to me everything there is to know about this fridge. I'm looking forward to asking you questions in the future. Jimmy Bagley, IA
• Wonderful service, prompt, efficient, and accurate. Couldn't have asked for more. I cannot thank you enough for your help. Mary C. Freshfield, Liverpool, UK
• This expert is wonderful. They truly know what they are talking about, and they actually care about you. They really helped put my nerves at ease. Thank you so much!!!! Alex Los Angeles, CA
• Thank you for all your help. It is nice to know that this service is here for people like myself, who need answers fast and are not sure who to consult. GP Hesperia, CA
• I couldn't be more satisfied! This is the site I will always come to when I need a second opinion. Justin Kernersville, NC
• Just let me say that this encounter has been entirely professional and most helpful. I liked that I could ask additional questions and get answered in a very short turn around. Esther Woodstock, NY
• Thank you so much for taking your time and knowledge to support my concerns. Not only did you answer my questions, you even took it a step further with replying with more pertinent information I needed to know. Robin Elkton, Maryland

• ### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer
< Last | Next >

### Mike

#### Satisfied Customers:

1425
Licensed Master Electrician - OnQ Certified Data Voice Audio Video Installer

### Jason

#### Satisfied Customers:

3871
Over 20 years of experience in all types of installations, troubleshooting, and repairs.

### Mike G.

#### Satisfied Customers:

6511
Proven Professional 46 years Experience

3264

### Kevin

#### Satisfied Customers:

2371
29 years as a Licensed Electrical Contractor in Illinois, 5 year college Electrical Instructor, Former Electrical Inspector, Diploma in Digital Electronics, Former Illinois Licensed Home Inspector

### electrifier

#### Satisfied Customers:

1458
Electrical contractor and electrical inspector for over 24 years with phone and networking expertise