That being the case, I would feed it with a 50 amp breaker, and #6 copper wire.

Jason :

If you are using THHN stranded building wire, it can be #8/

Customer:

can you provide the formula that you used

Jason :

Sure. Volts X Amps = Watts. We know the wattage is 7500, and the voltage is 208. So, just divide the watts by the volts, 7500/208 to arrive at 36 amps.

Customer:

watts divided by volts--x 1.732 equals amps correct ??this is 3 phase

Customer:

are u there

Jason :

Thank you for your patience. I'm referencing my materials, as it's been a while since I had to determine when to use the 1.73 rule.

Jason :

Yes, you are correct. I was mistaken. 36 X 1.73 = 62.28. That would be a 70 amp breaker and #4 copper wire.

Customer:

ok---explain this:

Customer:

7500 watts at 240 volt SINGLE phase is 31.25 amps (watts divided by volts)---7500 watts / 208 volts=36.06 times 1.732 is= 62.46 amps----shouldn't the amperage on 3 phase be lower than single phase ???

Jason :

Now that I look at it again, I believe we are both misapplying the formula.

Customer:

what am i doing wrong ?

Jason :

We don't need to multiply the original amperage I arrived at by 1.73.

Jason :

That is to find watts.

Jason :

Wire is sized on amperage, not wattage.

Customer:

a 7.5 kw heater at 208 3 phase

Customer:

7.5 is 7500 watts

Jason :

Yes

Customer:

so only 7500 divided by 208 ??

Jason :

Yes.

Customer:

ok--thanks

Jason :

I apologize for being rusty, it's been a while since I've had to use the 1.73 rule.

Customer:

gues im done--nite

Jason :

If you don't mind standing by for a moment...

Jason :

I just found a site that explains it very well.

Customer:

so i just close this web site now ?

Jason :

I'll post a link after I view it.

Customer:

ok--go i go now ?? dinner is waiting

Jason :

You can go and come back later. No problem.

Jason and other Electrical Specialists are ready to help you

So, according to this info, you need to first multiply your voltage by 1.73. That comes out to about 360 volts. Then, divide your wattage by that number, which comes out to just over 20 amps.

So, I would run #10 wire, and put this on a 30 amp breaker.