i am runing sub panel for a kitchen serving line 240 sub panel sizing my to hot wires as #8copper main breaker to panel as a 40amp what size should my neutral be sized at safely
Hi, Welcome to Just Answer. My name is XXXXX XXX would be glad to assist.
If most of the load will be 240 volt breakers, then reduce to a #10 for neutral and ground.
If the panel will serve 120 volt breakers for the most part without know the load, keep neutral at #8 and ground at #10 to be safe
iwas not able to get back yesterday went ahead to use#8 for future exspansion most of the load will be 9.7 amp 240 circuits going with a 50 amp at main panel thankyou kindly for the information
Contractor-40 Years in the ElectricalTrade