I am replacing my pool timer with an ET1125C(r). Set for 120 Line, 120 load, and SPST IND. to no avail. I have hot to #2, nuetral from pump to nuetral bar, load from pump to #4. I get 120V to nuetral on # XXXXX but nothing anywhere else. What am I missing here?
Understanding the schematic!! lol
Welcome to just answer!
First Is the override Switch on?
do u understand my issue?
umm, where is this located?
Hi, I'm Mike and I'll be glad to assist you. Here is a sketch for the connections.
so, nuetral to #1 & motor & hot to #3 & #2?
As shown and set the Voltage to 120V on the voltage switch, so as to not fry the clock motor.
ok... but post#1 is for a second line, which I'll use for the second load(aux. pump).
You mentioneed nothing about a second load in your question. The statement was SPSTand that is what I gave you the diagram for. If you give me all the details, I'll rework it for you.
ok...2 lines(2 seperate circuits), 2 loads, 2 seperate timers, 120 in, 120 out.
Here you go.
I'll try it, be right back!
also, I need to set jumper to SIM? or IND?
If they share the same on and off time, then Sim. If not, then Ind.
Proven Professional 44 years Experience
your the man! It worked, thanks! XXXXX was missing was the jumper on post 2-3.
Very Good - Glad to help.