I put two 20 amp GFCI breakers in my service panel. These 2 GFCI's are split between 2 outlets w/ 12/3 wire. How do I connect the (1) common wire to the 2 seperate "common" lugs on the GFCI's?
Hello,I'm sorry but you can not have 2 single pole gfci breakers on 2 circuits which shares one neutral.What is 12/3 circuits for?
we have 2 - 20 amp breakers split between 2 outlets. Its in a utility shed, so we have to have GFCI's. Can I get a 2-pole 20 amp GFCI and use that as it will only require 1 common wire connected to it?
You can get 2 pole breaker or just get gfci outlets , it might be less expensive.