Table 310.15(B)(7) Conductor Types and Sizes for 120/240-Volt, 3-Wire, Single-Phase Dwelling Services and Feeders. Conductor Types RHH, RHW, RHW-2, THHN, THHW, THW, THW-2, THWN, THWN-2, XHHW, XHHW-2, SE, USE, USE-2
Conductor (AWG or kcmil)
Service or Feeder Rating (Amperes)
Aluminum or Copper-Clad Aluminum
Mike G. or whoever is available for an electrical question .......
My existing electrical box is currently 100 AMPS, the wire that feeds the box is smaller than 2/0 but is copper. If I put in 200 Amps panel box and use the same amount of breakers and not change anything (I know it is not suppose to be legal) what if anything will happen...would there be a problem or danger? What are your thoughts on this?
MIKE ....OK I AM FAMILIAR WITH ELECTRICAL AND HAVE DONE MY OWN ELECTRICAL BOX INSTALLATION AND GOTTEN COMPLIMENTS FROM INSPECTORS ....HOWEVER, I AM NOT FAMILIAR WITH SOME OF THE TERMS.....I AM CONFUSED BY WHAT A 'RISER' IS????? THANKS FOR THE INFO